YLW coal-fired: 1400-29000KW
Working pressure: 0.8-1.0MPA
Working media: Thermal fluid
Output temperature: 320°C
Available fuel: Bituminous coal, soft coal, biomass particles
Available industries: Chemical, fertilizer, melamine, alumina and other high temperature heating technology.
YLM thermal fluid heater is square coil horizontal chain stoker assembly heater, chain stoker and heater body are transferred separately. It adapts chain stoker to realize mechanical feeding coal, mechanical venting by blower and exhaust fan, and mechanical discharging by slag machine.
Fuel fall on the stoker by coal bucket during operating and burning, high temperature smoke enters furnace by passing combustion arch, after radiation heat exchange, smoke enters convection heating surface for convection heat exchange, then goes to waste heat boiler and air pre-heater, at last enters dust collector then vented into the atmosphere through chimney by exhaust fan.
full argon arc welding
long life span
We have combustion arch patent, which is available for different types of coals, even the soft coal is also very easy to burn.
Flame-proof feeding bucket, it can avoid the feeding bucket is burnt and coking.
There is ash cleaning unit, it is easy for maintaining, operating and cleaning.
Less fuel consumption
|Rated thermal power (KW)||kW||1400||1800||2400||2800||3500||4200||6000||7000||8200||4600|
|Design working temperature(≤℃)||320||320||320||300||320||320||320||320||320||320|
|Rated working pressure (MPa)||0.8||0.8||0.8||0.8||0.8||0.8||0.8||1.0||1.0||1.0|
|Thermal efficiency (≥%)||80||80||80||80||80||80||80||80||80||80|
|System installation power (KW)||55||63||76||85||105||125||155||170||193||150|
|Expansion tank m3||2.5||2.5||2.5||3.5||3.5||5||5||8||10||15|
|Fluid storage tank m3||5||6||6||8||8||10||10||15||15||25|
|Rated thermal power (KW)||kW||9400||10500||12000||14000||16500||18000||21000||23300||26000||29200|
|Design working temperature(≤℃)||320||320||320||320||320||320||320||320||320|
|Rated working pressure (MPa)||1.0||1.0||1.0||1.0||1.0||1.0||1.0||1.0||1.0|
|Thermal efficiency (≥%)||80||80||80||80||80||81||81||81||81|
|System installation power (KW)||160||260||320||380||450||520||600||700||825|
|Expansion tank m3||15||20||20||30||30||30||30||30||30|
|Fluid storage tank m3||25||30||30||40||40||60||80||80||80|